Point Manager for BACnet
The Point Manager view is available for each device added to the BACnet network. It lists all BACnet Points added to the Device component, and shows their Out slot value, status, object name and ID, polling mode, and enabled or disabled state.
Opening the Point Manager
The Point Manager view is accessible from the context menu of the Device component. It is also automatically opened if the Device component is double-clicked in the Workspace Tree window.
Adding BACnet Points
The BACnet points may be added to the device twofold: dragging and dropping the BACnet points to the Device component from the BACnet library (in the Device Libraries window), or using a special Add function in the Point Manager view available in the bottom right corner. The Add function allows to add any of the BACnet points available in the BACnet library.
Using this Add button opens the dialog window, which allows to adjust the quantity of BACnet Points to be added.
Multiediting of Common Slots
The Point Manager view allows multiediting of common slots in components of the same type, for example, to enable all one-type components at once. Multiediting is available in the Object Properties window, upon selecting one-type components in the Point Manager with Ctrl or Shift keys.