The occupancy mode setting is available from the main menu level. If the room panel is in the active mode, pushing the OK button once leads the user to the occupancy edit submenu. On the 14-segment display block, flashes the “OCCM” text (with a frequency calculated on the SUBMENU_ICON_FLASHING_TIME basis), and on the 8-segment display block, the name of the current OCCUPANCY_MODE is displayed.
OCCUPANCY_CURRENT_STATUS (MV 3)
This object contains a numeric value corresponding to the current occupancy status. The particular object values are the basis for displaying the specific group of icons (see the table below). The object value can be used as the current occupancy status indication. The default value of this object is 1.
Human symbol blinks
OCCUPANCY_MODE (MV 4)
This object contains a numeric value corresponding to the occupancy mode. There are two different occupancy modes, which can be selected locally from the occupancy edit submenu level (see the table below). To enter the occupancy edit submenu, push the OK button when the room panel is in the active mode. Default texts for particular occupancy modes can be changed.
Text on LDC
OCCUPANCY_MODE_NAME (MV 4, State Properties)
For user-friendly use, the OCCUPANCY_MODE object value is displayed on the LCD as text instead of a numeric value. The name can be set up in the state properties. There are two occupancy modes, which can contain up to 4 characters according to the ASCII code.